IEC Edition INTERNATIONAL. STANDARD. Surge arresters –. Part 5: Selection and application recommendations. INTERNATIONAL. IEC is not a mandatory standard but provides information, guidance, and recommendations for the selection and application of. IEC Edition INTERNATIONAL. STANDARD. Surge arresters –. Part 5: Selection and application recommendations. IE. C. 9. –
|Published (Last):||18 June 2018|
|PDF File Size:||14.45 Mb|
|ePub File Size:||12.36 Mb|
|Price:||Free* [*Free Regsitration Required]|
The user of surge arresters will, in that case, not be required to apply the whole process introduced here to any new installation and the selection of characteristics resulting from prior practice may be continued. Surge protective components, current at the date of this publication. Our prices are in Swiss francs CHF. Also 60909-5 details of pollutant compositions and methods of application and the procedures associated with each mode of pollution.
Please download Chrome or Firefox or view our browser tips. Surge arresters – Part 5: This is a first for arrester standards harmonization.
Artificial pollution testing of surge arresters This standard gives the basic principles of artificial pollution testing of non-linear resistor type valve type surge arresters. These considerations apply specifically to electric utility systems and do not recognize the neutral grounding requirements for dispersed storage and generation. It has been years in the making. The way these transmission-line choices will improve or degrade lightning performance is also provided. Surge arrester residual voltage is a major parameter to which most users have paid a lot of attention to when selecting the type idc rating.
Accept and continue Learn more about the cookies we use and how to change your settings. Shopping cart Close cart 0, foreach: Definitions, principles and rules This part of IEC applies to three-phase a. Message to your colleague. Functional requirements for 6099-5 devices, maintenance, design and production tests, and a guide for operation are included.
Sustainable Development Goals and standardisation, how do they connect? An additional section discusses several special methods that may be used to improve lightning performance.
Selection and application recommendations Status: TC 37 – Surge arresters rss. Part 1 covers the insulation surge withstand strength of motors and generators with windings having form-wound multi-turn coils and the application of surge protection to form-wound multi-turn coil motors. Worldwide Standards We can source any standard from anywhere in the world. You may experience issues viewing this site in Internet Explorer iwc, 10 or It covers phase-to-phase, phase-to-earth and longitudinal insulation of three-phase systems with nominal voltages above 1kV Preview Insulation co-ordination – Part 4: You may find similar items within 06099-5 categories by selecting from the choices below:.
September Replaced By: In many cases, the prescribed steps are adequate. The guide does not cover motors applied in solid-state switched adjustable speed drives.
This edition includes the following significant technical changes with respect to the previous edition regarding the new surge arrester classification introduced in IEC Take the smart route to manage medical device compliance.
IEC | IEC Webstore
Metal-oxide surge arresters with external series gap EGLA for overhead transmission and distribution lines of a. The methods of analysis are illustrated by practical examples. It specifies the procedure for the selection of the rated withstand voltages for the phase-to-earth, phase-to-phase and longitudinal insulation of the equipment and the installations of these systems.
Surge arresters and low-voltage limiters for specific use in d. Its object is to give information in terms of methods, modeling and examples, allowing for the application of the approaches presented in IECand for the selection of insulation levels of equipment or installations, as defined in IEC Do you need a multi-user copy?
BS EN – Surge arresters. Selection and application recommendations
This standard recommends that the selected withstand voltages should be associated with the highest voltage for equipment. In Annex J, some aspects regarding the old type of SiC gapped arresters are discussed. Functional requirements for protective devices are addressed, including varistors and bypass gaps.
Surge arresters – Part 5: Selection and application recommendations
Glossary of terms and definitions from 600999-5 publications,, and This standard provides a list of terms and definitions relative to IEC publications from IEC technical committee Click to learn more.
This new edition covers new mechanical test requirements for polymer and porcelain housed arresters. Non-linear resistor type gapped surge arresters for a. Your basket is empty.
BS EN 60099-5:2013
ifc Valid Buy this standard. The designer may exercise control over structure material and geometry, shielding if anyamount of insulation, grounding, and placement of arresters. Protective equipment for series capacitor banks This part of IEC covers protective equipment for series capacitor banks, with a size larger than 10 Mvar per phase.
The uec for human safety are not covered by this standard. Grounding electrode techniques, pole ground values, and system ground grid values are not addressed or considered in this document.
Your shopping cart is empty. Though it will be many years before the both standards are virtually the same, this is a first step.